What makes a good air conditioning contractor? Believe it or not, the best air conditioning contractor is the one you rarely ever have to see. You might be able to save some money in the short term by hiring a second-rate company to take care of your AC system, but you’ll wind up having them out to your Tampa FL home every few months for another expensive repair because they aren’t doing the work with the commitment to quality you expect. Or worse, they vanish into thin air and leave you holding the bill for work they aren’t around to back up. That is a long-term expense you simply can’t afford.
You want to know what else is long-term, though? We are. Harrington AC has been here since 1979, and many of our employees have been with us for decades. We have customers that are on their second, or even third, system with us. That kind of longevity confers a value that you can’t get from just any HVAC company. We’ve been around, we’ve seen how the technology is changed and we’ve adapted every step of the way. We’ll be here long after the work is done to stand behind it and guarantee your satisfaction. Most importantly – you shouldn’t have to see us much at all. Don’t get us wrong, we love visiting our customers and see them like family – but we also aim to do work of such quality that you’ll never have to worry about your comfort.
You can see that thread through the reviews our previous customers have written for us. In Tampa, FL and beyond, they’re all saying the same thing – when you call Harrington AC, you’re getting more than your money’s worth. You’re getting a company you can rely on through thick and thin – or in our case, warm and cold. Explore the pages below to read reviews from your hometown neighbors and those in surrounding areas and see what they have to say about Harrington AC. Then give us a call at 727-541-5222 to put us to work for you.
for Tampa, FL
Our Reviews by City
Daven - Tampa, FL 33602
On time! Checked everything! Got the job done!!
Found no power supplied to condenser unit. Found breaker to have popped. Reset breaker and tested system finding no shorts to ground. System cooling and draining well at this time. Poured water down drain line and confirmed system is draining. Homeowner aware filter needs to be changed asap and should be changed monthly.
Found no display at thermostat due to corroded batteries, requires new thermostat. Also found blower motor & MMC board failed and needing to be replaced. Unable to check the rest of the system operation due to the fan not working. Unable to guarantee that these repairs will get system up and running properly. Recommend replacing equipment due to age and cost of repair. Also blower motor assembly is on back order and unable to confirm when we will actually be able to replace motor if customer goes with repair.
Remove broken belt and replaced with A-47 belt for unit WA32. Tested operation and found system cooling well. Moved thermostat from office area to printing area where unit WA39 is located and actually cooling. Tested operation. Moved thermostat for WA42 from area where printing products are being held to office space that is directly on other side of the wall. Tested operation and found system cooling well. This is the system we just replaced. Alter duct work for unit WA38 to divert more air to managers office. Found that all systems need air filters changed. Informed management. Recommend changing filters monthly.
Performed diagnostic for WA32 and found broken belt. Need to return with A47 belt. Customer would also like WA39 thermostat to be moved from office area to printing room where unit is actually cooling. Found WA43 RTU with a broken fan blade for the condenser fan motor. System is in very poor shape and recommend replacing. Found condenser WA40 on roof not connected to an air handler. Line set is just cut and loose in ceiling. Unit was replaced by WA39 Found condenser WA36 on roof with no air handler. Line set had been cut and just loose in ceiling. WA42 (new system just installed) needs thermostat moved to inside wall of office. WA41 has no filter in it. WA38 need to return with sheet metal to divert air into managers office.