What makes a good air conditioning contractor? Believe it or not, the best air conditioning contractor is the one you rarely ever have to see. You might be able to save some money in the short term by hiring a second-rate company to take care of your AC system, but you’ll wind up having them out to your South Pasadena FL home every few months for another expensive repair because they aren’t doing the work with the commitment to quality you expect. Or worse, they vanish into thin air and leave you holding the bill for work they aren’t around to back up. That is a long-term expense you simply can’t afford.
You want to know what else is long-term, though? We are. Harrington AC has been here since 1979, and many of our employees have been with us for decades. We have customers that are on their second, or even third, system with us. That kind of longevity confers a value that you can’t get from just any HVAC company. We’ve been around, we’ve seen how the technology is changed and we’ve adapted every step of the way. We’ll be here long after the work is done to stand behind it and guarantee your satisfaction. Most importantly – you shouldn’t have to see us much at all. Don’t get us wrong, we love visiting our customers and see them like family – but we also aim to do work of such quality that you’ll never have to worry about your comfort.
You can see that thread through the reviews our previous customers have written for us. In South Pasadena, FL and beyond, they’re all saying the same thing – when you call Harrington AC, you’re getting more than your money’s worth. You’re getting a company you can rely on through thick and thin – or in our case, warm and cold. Explore the pages below to read reviews from your hometown neighbors and those in surrounding areas and see what they have to say about Harrington AC. Then give us a call at 727-541-5222 to put us to work for you.
for South Pasadena, FL
Our Reviews by City
Carl - South Pasadena, FL 33707
Collin was very thorough and was able to answer all my questions. I was very happy with his service.
Robin - South Pasadena, FL 33707
I have always received superb service from Harrington and today was just as superb. Jordan was professional, efficient, knowledgeable, and patient. He explained everything thoroughly and went beyond the call of duty. Outstanding!
Becky - South Pasadena, FL 33707
Becky - South Pasadena, FL 33707
Found multiple issues with system, recommend repair or replace before it completely fails. Need to return to install new filter. 24”x21” Trane filter. See attached pics for filter exact size
Checked pressures, temperatures, amp draws, and cleanliness. All within factory specifications. Flushed drain assembly and added pan algae tablets. System is working and draining properly.
Upon arrival found outdoor unit not running at all. Checked capacitor found capacitor to be bad. Replaced with new 45x05 capacitor. Checked system operation. System operating to manufacturer specifications. Put pan tabs in condensate pump. talked with customer about maintenance plans. Customer will consider.
Replaced rusted pan with new pan. Checked pressures, temperatures, and amp draws. All within factory specifications. Flushed drain assembly. System is working and draining properly. System cleanliness is great. No issues with anything at this time.
Includes: clean existing refrigerant lines with nitrogen, new emergency float switch at coil, seal around condenser when done, removal and disposal of existing equipment, taxes and permits. Warranty: Condenser- 1 yr labor, 2 yr parts, 5 yr compressions / Coil- 1 yr labor, 10 yr coil
Need to return with 66” x 30” horizontal pan. Also when work is complete need to put together a summary that everything is in good standing for home inspector.
Performed check up included in maintenance plan. Found no other issues. System operating with in design specifications. Customer did request we look into getting her a filter door that comes with the air handler as hers is missing. Please give customer quote if we can get one.
System cooling poorly at this time and was produced in 2006. Suggested replacement due to age and condition, scheduled for Barry to provide estimate as this is a through the wall condenser and I am unable to provide pricing today.
On arrival found the outdoor unit off. Replaced with new capacitor. System operating normal.
Upon arrival found unit off to primary saftey switch. Pulled out clogged filter(14x18x1). I believe the unit froze over due to the dirty filter. Changed out breakers for correct breakers. System operating to manufacturer specifications at this time.
Upon arrival unit was off and customer could hear noise of air blowing. Preformed diagnostic and found no connection between AC unit and the noise coming from the top of the AH closet. Collected diagnostic.
Found system running and cooling, drain pan holding water causing float to trip in evening when condensation is produced the most. Clear drain and now system operation is normal and cooling. Explained to customer we are not responsible for stack drain.
Recover refrigerant and removed compressor. Installed OEM compressor under part warranty. Pressure tested and evacuated system. Added 5.5 lbs of refrigerant to achieve proper refrigerant pressures. Also removed and replaced failed Honeywell pro5000. Checked unit operation and found no other issues. System cooling properly.
Found compressor not running with the operation of the rest of the system. Failed run cap was the cause of compressor not coming on. Replaced failed cap with 40mf run cap. Started system and checked full operation, pressures and all amp draws are within factory specs. System operation is normal and cooling at this time.
Upon arrival system was off due to primary switch. Cleaned and flushed drain line with shop vac, water, and drain cleaner. System operating properly at this time.
Upon arrival outdoor unit not running. Checked power at Contactor. 0vac. Flipped the breaker and system operation normal. Did overview of the system found no additional faults. System operating to specifications at this time.
Found system to be low on refrigerant. Provided estimate for replacement and homeowner decided to recharge system for now. Homeowner aware quote for replacement is good for 30 days and may change after according to equipment costs and availability. Recharged system with 2.7 # 407c , system now cooling well
Found breaker for air handled flipped to off position. Turned on breaker and tested system operation. Found system to be cooling poorly, checked refrigerant pressure and found extremely high suction pressure and compressor with very low amp draw reading. System needs compressor replacement and full refrigerant charge. Thermostat operating however 7 segment display not showing up on the left side of the 8 portion. Found batteries installed in thermostat with common wire in place. Removed batteries today. When batteries are not required to operate thermostat batteries will often fail and damage thermostat, found corrosion of battery terminals showing signs of this happening in the past. Called homeowner and left message as there was no answer.
Found a wire yellow connected to board, not activating, yellow cool speed only intermittently due to faulty furnace board ramping between fan and cool speed, wire intermittently need new board one man one hour recommend using speed 4 I put on the fan pin for cooling ,system was on Gray wire speed five which was 1150 CFM only 2 1/2 ton very loud Replaced control board. system is working and draining properly. 8-23-2023.
Checked airflow, ductwork, pressures, temperatures, and amp draws. All within factory specifications. System is working and draining properly. Notified customer to replace filters and that windows are allowing heat into the house. System is also undersized for house.
Reforms check up. Check voltage and amp draws across the system. Checked refrigerant. Pressures and temperatures. Checked drain line. System operating to manufacture specifications at this time.
Found unit to have several issues, recommended replacement at this time.
GOODMAN REPLACEMENT SYSTEM 14.3SEER2 STRAIGHT COOL CONNECT TO EXISTING HIGH-VOLTAGE, LOW-VOLTAGE, DRAIN, LINESET, AND DUCTWORK. ALL PERMITS AND INSPECTIONS INCLUDED. 10YR PARTS 1YR LABOR WARRANTY