For Air Conditioned Comfort In Your Seminole, FL Home - Call In The Experts
At Harrington AC, air conditioning is our passion! Bringing comfort and peace of mind to the people of Seminole, FL since 1979, we have cemented ourselves as an honest and reliable air conditioning repair, installation and maintenance company. By never cutting corners or taking shortcuts on quality service, Harrington AC goes above and beyond when it comes to all of your air conditioning needs. Plus that's not all! From air purifiers to air filters, the team at Harrington AC offers a variety of indoor air quality solutions so you can enjoy a clean and healthy home. Whether you're looking for a simple maintenance plan or need direct assistance, you can count on the dedicated professionals of Harrington AC!
Find Out What Your Neighbors Think!
At Harrington AC, air conditioning isn’t just our job – it’s our passion! Our dedication to providing quality service and top-notch customer satisfaction shines through in every air conditioner we install. We take great pride in the wonderful feedback we receive from our fans. Everyone in the Seminole, FL area loves being cool and comfortable with air conditioning from Harrington AC! When you're ready to experience premium air conditioning for yourself don't forget – Harrington AC is here for you! Check out the reviews below to get a glimpse of what your neighbors are saying about us, then call 727-541-5222 today!
for Seminole, FL
Our Reviews by City
Tom - Seminole, FL 33777
Tony and Johnny did a great job with the installation of our new Daikin Fit Variable Speed Heat Pump System (compressor and air handler).
Tom - Seminole, FL 33777
Great job! Thoroughly professional and attentive to our needs.
Terry - Seminole, FL 33777
Brian J was very efficient and professional. He gladly shared advice about ongoing mice. I hope he can service my system again in the future.
Mario - Seminole, FL 33777
I want to thank the technician he was on time earlier than I expected. I need to do a good job.
Judy - Seminole, FL 33778
Adam is very professional and personable. He takes time to answer questions and is very knowledgeable. I’d love to have him do my next service
Robert - Seminole, FL 33776
Tanner was on time, very polite & professional. Good job.
Jean - Seminole, FL 33777
Carolyn - Seminole, FL 33772
Jordan did a great job explaining and performing AC maintenance service. Very professional 🙂
Kerri - Seminole, FL 33772
He was very courteous nice explaining the job to me and did a really good job. I’m having no problems so far I’d recommend you guys especially him to others.
Kim - Seminole, FL 33772
Tanner did a great job. Very happy with the service.
John - Seminole, FL 33777
Vince was great! He diagnosed the problem and fixed it right away.
James - Seminole, FL 33777
My AC was not working and Harrington was able to send someone out to fix it the same day I called. The tech was great and explained the issue.
Excelente service and excellent Technician
Horacio - Seminole, FL 33772
Prompt n pleasant
Jeff - Seminole, FL 33772
Colin is a fine young man, respectful in every way, and who I believe, is an asset to Harrington future .
Wayne - Seminole, FL 33772
Jodan was a very knowledgeable and courteous young man! He was on time, looked professional and was very polite. He answered all my questions and his goal was to make the experience a good one. This young man gets what customer service is all about and my recommendation is he's a keeper. I will be recommending your company to my friends and family.
Irene - Seminole, FL 33777
Brian was very nice and professional
Timely, friendly service.
Jan - Seminole, FL 33777
Was very pleased with today’s AC service. This will give me peace of mind as we endure the remaining hot months of the year.
Great service, wonderful personality, punctual, explained everything clearly. Great record keeping of past services.
Nancy - Seminole, FL 33777
David - Seminole, FL 33777
Paul - Seminole, FL 33777
excellent response from Jane at H.A/C Communication with her was excellent - she was genuinely concerned with my A/C issue. Vince was likewise very efficient and was able to provide a solution to my A/C issue.
Justin provided great service
Leah - Seminole, FL 33772
Justin is a pleasant and knowledgeable service technician. Please assign him to any jobs for my address.
Jim - Seminole, FL 33772
Very good tech knowledgeable
Attention to detail
Scott - Seminole, FL 33772
I was having an issue with cooling for quite some time. Another company had been out a couple times and performed basic tests but never actually diagnosed the problem. Brian spent time performing various tests and looking at some of the ductwork to get to the root of the problem.
Sarah - Seminole, FL 33777
Collin was very helpful and answered all my questions. It was a very positive visit.
Very good and quick response
Randy - Seminole, FL 33776
Found leak on condenser coil. Added 3.5lbs 410a to find leak. Client accepted repair, so we will order it and when we get a delivery time, we will call to schedule repair.
Found condenser not running due to float switch being tripped from clogged drain line. Flushed condensate, now flowing free and clear. Checked all amp draws and pressures, all are good and within factory specs. System operation is now normal and cooling at this time.
12YR PARTS 12YR LABOR WARRANTY THROUGH MANUFACTURER. CONNECT TO EXISTING LINE-SET, DUCTWORK, DRAIN, HIGH AND LOW VOLTAGE WIRING. NEW DISCONNECT AND WHIP AT CONDENSER UNIT. WHOLE HOME PURIFIER.
Found bad capacitor not letting unit run. Replaced and tested, unit up and running but not perfectly. Replacing unit due to age of unit and concern of how long it will last.
Found capacitor faulty on compressor terminal. Replaced capacitor and tested system operation. System now cooling well at 21 degree split temp. Homeowner elected to sign up for Harrington happy home program today.
Preformed 1 of 2 Maintenance inspections included with Basic Maintenance Plan. Checked through entire system including Temperatures, Pressures, amp draws, sub cool and super heat. Cleaned entire drain pan and completely flushed line-set. System is operating within factory specifications. No issues at this time.
Performed maintenance today testing amp draws, voltage, refrigerant pressure, capacitor and emergency float switch. Vacuumed drain line, treated drain with chemical cleaner , treated evaporator with no rinse coil cleaner and added drain tablets to internal drain pan. Homeowner elected to renew Harrington happy home plan today.
Found system with water in emergency float switch. Vacuumed drain line , treated drain with chemical cleaner and tested system operation. System cooling well at 20 degree split temperature. Homeowner elected to sign up for Harrington happy home plan today. Homeowner requests paper copy of invoice mailed to him.
Gave estimate for ductwork
Found damaged duct work. Quoted for both repair and replacement. Emailed pricing to customer.
Performed maintenance, found no problems. Flushed condensate line and pan, flowing free and clear. Checked all amp draws and pressures, all are good and within factory specs. System is running and cooling at this time.
Reformed check up. Checked refrigerant, pressures and temperatures. Check voltage an amp draws across the system. Cleaned and push drain line with shop vac and water. Put pan tags into air handler drain pan. System operating to manufacture specifications.
Performed check up. Checked refrigerant, pressures and temperatures. Cleaned and flush drain line with shop vac and water. Check voltage and amp draws across the system. Checked Reme halo operation. System operating to manufacture specifications at this time.
Performed maintenance on both systems. Tested amp draws, voltage, refrigerant pressure, capacitors and emergency float switch. Vacuumed drain lines , changed filters, added drain tablets to internal drain pan and treated evaporator coils with no rinse coil cleaner.
Replaced capacitor shorted and putted n Burt contacts ..Test system operation ,cleared and clean drain line out as a precautionary check filters system is working as designed after service thank you very much we will come out in six months and do our maintenance check up.outdoor disc box is rough..Thanks Vincent
Preformed 1 of 2 maintenance inspections included with Basic Maintenance Plan, checked through entire system. Including temperatures, pressures and amp draws. Completely cleaned drain assembly and flushed line-set. Noted weak 40/5 MFD capacitor, recommended replacement. Collected HHH fee.
Check system both heat and cool clean out drain line check thermostat operation both heat and cool system is cooling and draining customer keeps a thermostat set at 69°.health reasons. This is maintenance 1 of 2 one more maintenance visit per contract . Thank you.
Replaced blower motor and tested, unit operating properly at this time. Recommend having condenser coil cleaned.
Gave another estimate requested by the customer.
Gave estimate for replacement
After hours serviceFound the condensate pump busted and pumping water into the garage customer shut unit off and waiting for a response. Answering service said because this was a new unit there would be no charge his words.Replace condensate pump flushed out drain line and internal drain pan as long as well as added algicide tablets to the system checked refrigerant charge capacitors electrical everything is running as designed after service. There are no free service calls except during regular hours on new equipment. Thank you very much Vince.
Replaced thermostat wire from air handler to condenser first year warranty
Preformed Second Maintenance Inspection included with Basic Membership. Checked through entire system, including temperatures pressures and amp draws. Cleaned out entire drain pan and line-set. Talked with customer about Condenser Capacitor, was reading 28.4 and just barley still inside factory specifications. Also after finishing the drain cleaning the TXV started back flowing refrigerant. Also mentioned to customer about possible replacement.
Check system operation found a half ounce of water in the float assembly float switch was adjusted all the way down for maximum sensitivity I raise the float switch up as it will not be so sensitive and a couple drops of water won’t set it off system is cooling and draining well we flushed out and cleared the drain line as a precaution and check refrigerant levels as well as system operation on the outdoor unit..no charge per serv mgr. thanks Vince.
Upon arrival found outdoor unit not running at all. Found capacitor is bad. Replaced with new 45 µF capacitor. After replacing found out Outdoor fan motor, not running. Found it to be bad. Replaced with 825 rpm condenser motor. System operating to manufacturer specifications.