What makes a good air conditioning contractor? Believe it or not, the best air conditioning contractor is the one you rarely ever have to see. You might be able to save some money in the short term by hiring a second-rate company to take care of your AC system, but you’ll wind up having them out to your Madeira Beach FL home every few months for another expensive repair because they aren’t doing the work with the commitment to quality you expect. Or worse, they vanish into thin air and leave you holding the bill for work they aren’t around to back up. That is a long-term expense you simply can’t afford.
You want to know what else is long-term, though? We are. Harrington AC has been here since 1979, and many of our employees have been with us for decades. We have customers that are on their second, or even third, system with us. That kind of longevity confers a value that you can’t get from just any HVAC company. We’ve been around, we’ve seen how the technology is changed and we’ve adapted every step of the way. We’ll be here long after the work is done to stand behind it and guarantee your satisfaction. Most importantly – you shouldn’t have to see us much at all. Don’t get us wrong, we love visiting our customers and see them like family – but we also aim to do work of such quality that you’ll never have to worry about your comfort.
You can see that thread through the reviews our previous customers have written for us. In Madeira Beach, FL and beyond, they’re all saying the same thing – when you call Harrington AC, you’re getting more than your money’s worth. You’re getting a company you can rely on through thick and thin – or in our case, warm and cold. Explore the pages below to read reviews from your hometown neighbors and those in surrounding areas and see what they have to say about Harrington AC. Then give us a call at 727-541-5222 to put us to work for you.
for Madeira Beach, FL
Our Reviews by City
Includes: whole home air filter, secondary vertical pan w/float switch, clean exterior refrigerant lines with nitrogen, new float switch, removal and disposal of existing equipment, taxes and permits. $395.59 service credit is applied to price. Warranty: 12 year parts and labor.
Sold job for Daikin 1.5 ton Platinum Heat Pump system $12908. Customer paid half down by card $6,454. Install planned for Wednesday
Found blower motor running upon arrival. Found evaporator coil dirty and needing a cleaning. Found condenser not running due to a shorted capacitor. Also found oil residue and signs of a leak on the subcool loop of the condenser coil. Also found cracked high pressure switch. Liquid line drier and muffler is rusted and needing to be replaced. Compressor is also rusted. Recommend replacing equipment over repairs. A leak check would be required to determine if anything else is leaking. Gave customer 3 estimates on replacement systems.