Exceptional Air Conditioning Service in Dunedin, FL
Living in Florida may bring about hot, humid days during the summer, but Harrington AC has been providing air conditioning repair, installation and maintenance services to keep you cool since 1979. For over 40 years, we have been pridefully using our expertise to take care of our customers with the utmost quality and dependability. Other air conditioning companies may come along and cut corners to save money, but Harrington AC brings nothing but first class air conditioning service in Dunedin, FL. Don't forget that we also offer heat pump and indoor air quality solutions to improve the air in your home. Sign up for our Total Comfort Agreement maintenance plan today and let Harrington AC show you why we're the best!
Find Out What Makes Harrington AC Different
At Harrington AC, we take pride in customer satisfaction. Our goal is to be your air conditioning go-to service so that you can always relax knowing you will get the best and most reliable air conditioning services around. So take a few minutes and listen to what our amazing fans have been saying about our air conditioning service in Dunedin, FL! Our satisfied customers are raving about the quality work we do and giving us glowing reviews. Check out their testimonials on the pages below, and when you’re ready don’t hesitate to give us a call at 727-541-5222 !
for Dunedin, FL
Our Reviews by City
Excellent customer service!
Jessica - Dunedin, FL 34698
Found house temp satisfied to set temperature on thermostat upon arrival. Ran system and found no problems. Checked all amp draws and pressures, all are good and within factory specs, system is running and cooling great for age with a 22 degree split. Customer said outdoor unit was making noise a day prior, but stopped making noise same night and hasn’t made the noise again. Found no cause for a noise at outdoor unit. System is running and cooling at this time.
Found 3 ton Goodman package unit very low on Freon. Found visible outdoor coil condenser coil leakage due to out of warranty condition. Not worth repair. Customer needs free estimate on new unit.
Found Bryant 2 ton split cycling on drain safety switch causing abnormal operation. Gave customer quote on cleaning drain and pump. She will wait and try to do her self. Recommend getting twice a year maintenance gave estimate on happy home plan tested operation of unit while running unit operating normal probable noises heard were due to float switch cycling, causing abnormal compressor backwards run Possible all noises were normal during service call
On arrival found system off to secondary switch. Cleaned and flush drain line with shop vac drain solv, and water. Cleared water from secondary pan. Installed a drain guard for customer. System operating to manufacture specifications at this time.
Replaced air handler circuit board verified air filter was replaced on August 3, 2023
Air Conditioning Repair Service near Inverness Dr. We were contacted by a homeowner in need of assistance with their non-operable air conditioning system. I promptly arrived at the residence to address the issue. After examining the system, I suspected the problem to be a refrigerant leak, so I completed a UV dye insertion to determine where the leak originated. After locating the leak I was able to seal it up and refill the refrigerant in the system to get it back in working order!
Air Conditioning System Installation near Robmar Rd. I was contacted by a residential client that needed a new air conditioning system for their home. I arrived after a consultation to install a new Goodman ductless mini split air conditioning system into the home. I carefully checked each component of the system and ensured that it was operating within the manufacturer’s recommended specs. The client was grateful to have a reliable source of cool air for the coming summer heat.
Indoor air quality service call. Performed whole home humidifier installation and UV light installation on their HVAC system to improve overall air quality.
AC Maintenance visit. Customer has a 3 year old Carrier system. Went through entire air conditioning maintenance checklist, checked all components for proper operation, cleaned up the unit, checked electrical connections. Everything looking good.
Air conditioning maintenance service call. Customer getting yearly AC maintenance to make sure their system is ready to go for summer. Went through entire checklist, checked all components of system, everything looks good.
AC repair service. Customer's unit was no longer putting out cold air. performed air conditioning repair diagnostic checklist and determined the compressor was not working. Replaced the compressor and tested system for proper operation. Everything working correctly now.
Indoor air quality visit. Performed UV light installation for air purification. Advised customer of other indoor air quality options.