AC Repair, Replacement, Installation & Maintenance Services in Clearwater, FL
If you're looking to beat the Florida heat, there's only one air conditioning team you should trust in Clearwater, FL - and that's Harrington AC. Since 1979, families have relied on our dependable residential air conditioning repair, installation, and maintenance services!
AC Installation & Replacement Services
The Clearwater area can be unbearably hot and humid during the summer months, making a reliable and efficient air conditioning system an essential part of any home. When it comes to AC installation and replacement services in Clearwater, Harrington AC has been installing and replacing AC units in Clearwater since 1979!
That means you receive the most professional and high-quality services available. We have experienced HVAC technicians who can install or replace your AC unit quickly, ensuring that you have a reliable and energy-efficient system in place to keep you comfortable all year round.
Keep Your Clearwater, FL Home Cool With Harrington AC
We know how important air conditioning services is to Floridians and go above and beyond when it comes to taking care of our customers with friendly service, expert knowledge, and a commitment to doing things right every time.
Whether you need a new installation, a replacement, or just routine maintenance, Harrington AC is committed to providing exceptional customer service and top-quality workmanship to each and every customer.
Plus, don't forget our heat pump expertise or the custom indoor air quality solutions we can provide. It's no wonder why Harrington AC is your go-to air conditioning specialist in Clearwater - we're dedicated to keeping your home comfortable all year long!
The real worth of repairing an AC depends on a number of possible factors, including the unit's age and condition, the cost of the repairs, and the AC's anticipated lifespan. If the AC is not too old (new to around 15 yrs.) and the cost of repairs is not too high, it might be worthwhile to fix it. However, replacing the AC may end up being more cost-effective in the long run if it is old and in poor condition. To decide what to do in your particular situation, it is best to consult with a professional.
A leak in the refrigerant is the most frequent AC repair. This happens when there is a leak in the evaporator coil or refrigerant lines, which can make the air conditioner blow warm air or stop working altogether.
A clogged air filter is another frequent problem that can reduce airflow and make the AC work harder than it should, increasing energy costs and possibly causing system damage.
Other typical AC issues include faulty thermostats, electrical problems, and dirty condenser coils. These typical problems can be avoided with routine maintenance, such as changing the air filters and setting up annual tune-ups, which will keep your air conditioner in good working order.
See What Your Neighbors Are Saying About Our AC Repair Services!
At Harrington AC, air conditioning isn't just another job to us - it's our passion! We take every job we work on personally, and want to make sure each customer is satisfied with the results. That's why a great way to find out more about the different things that make Harrington AC stand out is to listen to what our fantastic fans have to say!
Our pages are filled with reviews from neighbors who have experienced what makes us different, and they tell us all the time how much they love what we do. Ready to join them? We're here for you, Florida! Call 727-541-5222 today!
for Clearwater, FL
Our Reviews by City
Michelle - Clearwater, FL 33762
Tanner was excellent! Very professional. Explained things in an easy to understand manner. Did a great job understanding my feedback and troubleshooting to find a solve.
Really excellent service!
Minou - Clearwater, FL 33756
The company was recommended to me and I am so glad I called. The experience in getting my air conditioner was really great. I didn’t feel that anyone was trying to convince me of anything I didn’t need. I called and the same day Barry came out to give me an estimate. And the day of the installation, I got a text to let me know that Malak and Max were on their way. They hauled all the trash off and I had nothing to worry about. I really appreciate the absolut great work from Max and Malak. These guys came on time and worked very efficiently. They were very professional and made me feel so comfortable, whenever I had questions Great job guys, I truly appreciate you! I guess, the company got stuck with me. And I will DEFINITELY recommend the company and these guys to anyone I know. This great service you unfortunately find less and less.
Debbie - Clearwater, FL 33755
Very thorough and great service.
Very happy with service and promptness
Karin - Clearwater, FL 33756
Jordan is an excellent representation of a professional, friendly, service oriented and pleasant to work with employee. I would request his presence in the future.
Terry - Clearwater, FL 33762
Jordan is a very knowledgeable technician...explained everything to me and was Very polite and professional.
Scott - Clearwater, FL 33756
Vince was great. He was friendly, knowledgeable, and kept a tidy work area. I would request him for future service and I would recommend Harrington to others. I would also recommend a break-down on the invoices of the cost of each part and labor like most companies provide.
Always a happy customer
Erin - Clearwater, FL 33761
I’ve been using Herrington for several years now and have always been satisfied with the service. Jordan did not disappoint today - thank you.
Air conditioning not cooling
Irma - Clearwater, FL 33767
Very happy with work and technician Tanner service . Total cost of repairs around 550 dollars.
Keith - Clearwater, FL 33764
Bruce - Clearwater, FL 33761
Technician was on time and corrected issue and inspected system to avoid future problems.
Janet - Clearwater, FL 33762
As usual, the service was exceptional. They were able to get a technician here the next day when my equipment was shutting off. Jeff was knowledgeable and courteous, and he explained an option that might work for me in the future. Thank you, Harrington.
Richard - Clearwater, FL 33767
Showed up on time, quick diagnosis, quick fix, very fair price. Even went above and beyond to fix a couple unrelated issues.
Barry - Clearwater, FL 33761
Friendly, patient and most importantly, competent. Couldn't ask for better.
Diana Sager - Clearwater, FL 33756
I interacted with Collin on behalf of the business where I am employed. His attention to detail and to finding the cause of the problem was exemplary. He provided service unparalleled in today's service industry. Based upon this service, I will be calling Harrington Air for my home needs.
Response from Harrington Air Conditioning:
It was a pleasure serving you and your work family. We really appreciate you taking the time to share your feedback and giving us such a glowing review.
Bruce - Clearwater, FL 33760
C Courteous Phone Staff in making appointment. Service Tech was prompt and Expert Service.
Patrick Klaskow - Clearwater, FL 33760
Mary - Clearwater, FL 33762
On arrival found compressor not running. Change failed 35 x 5 capacitor. Checked system operation. System operating to manufacture specifications. Talked with customer about system replacement, customer wants to proceed. Please call on Monday.
Preparation to replace warranty compressor removing holding charge. Found holding charge dropped off dramatically within minute indicating low Freon charge within system completed leak test found line set in chase under house leaking 7/8, 3/8 straight cool 50 feet will need to be replaced if problems removing line set because of routing From previous oaks in area may require external installation at high cost 9/28/23 removed old line set and under sized drain line. Installed new refrigerant line set, thermostat wire, & copper line for new condensate pump. Removed failed compressor and installed new compressor under part warranty. Installed new liquid line drier and suction drier. Pressure tested and evacuated system. Added 9lbs of refrigerant to achieve proper subcool. System is producing a 18 degree temperature split and is running within design specifications. Customer purchased maintenance premium plus plan and should have first check up in 5-6 months.
Preformed Maintenance Inspection included with Basic Maintenance Plan. Checked through both systems entirely. Including Temperatures, Pressures, Amp Draws, Sub Cool and Super Heat. Cleaned and flushed entire drain pan and line set. As well as removed water that was filling entire AUX pan. Both systems are operating within factory specifications. Cooling and draining properly at this time.
Changed out warranty blower motor. Cleaned blower wheel at no charge to customer. Checked system operation. System operating to manufacture specifications at this time.
Freeform check up. Check voltage an amp draws across the system. Cleaned in flush drain line with shop back in water. Checked refrigerant, pressures and temperatures. Checked accuracy of thermostat. Found humidity to be about 5% off. Adjusted for customer. Talked with customer about purifier being burnt out. Recommended replacing customer agreed. S/N: w3wrhL166 M/N: reme-h. System operating to manufacture specifications at this time.
Found system off on float switch, drain line was cleaned and flushed on June 21st, called Zion and he said customer was able to use one of her 2 maintenance visits. Collected $75 for Diagnostic. Checked through entire system. No further issues. System is currently draining and cooling properly. Quoted customer for condensate pump, should be added ASAP to prevent future drain clogs (PVC runs through 10+ feet of concrete slab from the 2nd floor of Town House)
Found system off on float switch. Performed drain cleaning. Checked pressures, temperatures, and amp draws. All within factory specifications. System is working and draining properly.
Found blower motor with proper high voltage and low voltage applied to it with no operation. Found blower motor/module failure. Wrote estimate to return and replace blower motor/module under part warranty. Also recommend we add a surge protector to help protect the motor from future issues. Customer paid $75 with check number accidentally did payed for all. Please call with eta asap. Also mail invoice to customer.
Performed maintenance inspection on both RTU units. Found no issues and system running with design specifications. Removed and replaced (4) 20x20x1 filters for the Lobby unit Removed and replaced (4) 25x20x1 filters for the Office unit
Dispatch fee only. Gave thermostat pricing, she is checking on getting her own instead, but if she decided to have us do it, she will call and let us know.
Found system with clogged drain line. Flushed drain assembly upon approval. Checked pressures, temperatures, and amp draws. All within factory specifications. System is working and draining properly. Customer purchased plus plan per Collin on 9-21-2023. Customer still has 2 of 2 inspections available.
Includes: Clean existing refrigerant lines with nitrogen, add condensate pump, electrician to add plug for condensate pump and add 230 volt circuit for heat pump air handler, cap gas line, new stand for air handler, check existing duct system, removal and disposal of existing equipment, taxes and permits. Warranty: 1 yr labor, 12 yr parts and compressor
Preformed 1 of 2 Maintenance Inspections included with Basic Maintenance Plan. Checked through entire system. Checked Temperatures, pressures, amp draws, super heat and sub cool. Cleaned entire drain pan and completely flushed line-set. Changed 16x20x1 filter. System is operating within factory specifications. System is cooling and draining properly at this time.
Preformed maintenance inspection 2 of 2 included with Basic Maintenance Plan. Checked through both system entirely. Temperatures, pressures, amp draws, super heat and sub cool. Completely cleaned drain pan and flushed entire line-set. Systems are both operating within factory specifications. Cooling and draining properly at this time. System #1 Needs Blower Motor Pull and Clean as well as Whole House Ionizer to prevent growth in cabinet. System #2 Needs Blower Motor Pull and Clean as well as Whole house Ionizer to prevent growth in cabinet.
Unit ran Friday for about four hours then cut out I believe to be on the float switch customer left for the weekend came back and the unit was cooling fine it was also cooling fine upon arrival trace amounts of water were found in the float switch made adjustments to the drain line where the float switch was attached so as it would not be so sensitive and or the air coming out of the unit would cause the float to flutter a.k.a. the bobber. No Em heater installed. ,
Preformed 1 of 2 Maintenance inspections included with Basic Membership. Checked through entire system. Temperatures, pressures and amp draws. Found no mechanical issues. Quoted customer for Blower Motor Pull and Clean.
Found compressor over heated and not running. Cooled compressor and added hard start kit. Also found disconnect arking and cause of issue. Remade connections and tested. Also reduced air flow to achieve a better temperature split and and remove more humidity.
Found some burnt wires on the capacitors in the outdoor unit note that the unit is 20 years old and do not recommend working on the machine nor putting that kind of money into it. Customer said due to his condition financially that he wants to try and do the repair and hope for the best against our advice. We’re Going to move forward with the repairs even though we cannot guarantee the outcome customer is aware of that and would like to try thank you very much Vince Replay starting components and system seems to be running OK at this time it is shifting from 1st to 2nd stage and both compressors are running after service refrigerant charge is OK and 19° temperature split customer can clean the condensate pump himself thank you
Perform complete maintenance vacuum drain line clean internal drain pan and add algicide tablets checked refrigerant charge emergency heat amps system is working well and in great condition maintaining 70° in the home
Found new drain line, sagging primary pan, supported new primary drain line so pan would not sag probable cause of going off on easy tea because drain was clear but didn’t note when flushed. Got big wad of white crap. Talked to customer about drainguard. Recommend drain guard customer will think about it
Estimate for replacement
Found system to be in horrible condition. The transformer is burned out in the air handler and someone has cut a lot of the wiring. Someone also replace the 3 phase contactor on the roof they could not make the unit run. upon arrival the disconnect was pulled out of the disconnect box in the attic and left inside the air handler. Due to age and condition ,the refrigerant being obsolete and low charge system is recommended for replacement rather than repair. Talked w Service manager Zion regarding this matter and he will get with the property manager thank you very much .
Upon arrival, system was set to off. Turned system on and checked through system operations. Checked super heat and sub cool. Along with temperatures pressures and amp draws. All within factory specifications. Notified customer, her system was turning off due to float switch and a clogged drain. Customer confirmed she could take care of the drain herself. Collected diagnostic fee and spoke with customer about membership plans.
Due to multiple issues found, we recommend system replacement at this time.
Perform complete maintenance clearing drain line and internal drain pan added algicide tablets clean the evaporator coil and condenser checked capacitors and amp draws system is working excellent in both heat and cool 19 to 20° temperature split AC 89° heat at 28 A no issues at this time